The incinerator shall also be equipped with special loading apparatus and mechanisms that allow safe incineration of
solid waste simultaneously with liquid sludge. Loading of solid waste could be achieved through bags.
All intermediate piping, bellows and other fittings for connection between the tanks
, burner, compressor and other equipment provided on the slide shall be provided by the successful bidder. Bidder shall
suggest connection points for sludge, DO and Hot water. Pipings up to those connection points are going to be on the charge of
the CEB. All equipment, such as pumps, blower fans, compressors and etc forming part of the incinerator lot will take
their electrical supply from an electrical panel. The panel should be equipped with proper circuit breakers
and contactors for each component and will allow independent padlocking of the equipment by operators without
intervening from interior of the panel. All padlocking works will be made from outside the electrical panel. The
Electrical panel will take supply from an outside 3 phase supply.
2.4 Electrical Panel
The panel nominal voltage shall be 415 Vac and its rated insulation voltage shall be 1000 Vac.
– The main compartment will be fed from an existing switchboard
The panel shall be of factory assembled, metal clad and draw-out type in design for outside application.